They are designed to cool the steam sample to the required temperature condition so the collected fluid can be further analyzed in a safely manner.
– Non condensable test
– Dryness test
– Superheat test
Performing tests involve establishing the physical attributes of dry saturated steam, the gaseous phase of water https://en.wikipedia.org/wiki/Steam
It is the steam supplied to steam sterilizers.
Non-condensable gases are the gases entrained in steam that do not condense back into water when the steam is cooled below its boiling point.Range limit is 0-3.5%
Steam dryness fraction is a value used to quantify the amount of water within the steam. For example if steam contains 5% water by mass, it’s said to be 95% dry, or have a dryness fraction of 0.95. Range limit is 0.95 to 1.0
The Superheat value is the temperature of the steam as it goes from steam line pressure to atmospheric pressure.Range limit less than 25 °C above the boiling point of water at your altitude.